Tektronix Technical Forums are maintained by community involvement. Feel free to post questions or respond to questions by other members. Should you require a time-sensitive answer, please contact your local Tektronix support center here.
My wiring diagram is attached. Is this an appropriate way to achieve my goal? I'd prefer not to blow up my equipment.
The "SHUNT" is simply a placeholder for *whatever* the meter has
"PLUG" is the input selected for test
The switch on the input side of CH41 is a manual switch. Just ignore it and consider it a different load than the one for CH42
- wiring diagram
- IMG_20160211_161120.jpg (787.35 KiB) Viewed 11033 times
- Keithley Applications
- Posts: 2845
- Joined: June 10th, 2010, 6:22 am
- Country: United States
The terminals for DCI and ACI are the AMPs(for HI) and INPUT LO for LO.
The INPUT HI and INPUT LO terminals are protected to 1000V through front panel terminals and 300V through switch cards.
The AMPs terminal is protected with an in line fuse at 3A and 250V.
From your set up , I would state the input is protected for all your voltage and current levels.
Hope this helps.
Who is online
Users browsing this forum: No registered users and 1 guest